Extremely professional and personable, work was efficient and accurate… yes, I would certainly use Mr. Sparky again and recommend them to friends.
Electricians at Mister Sparky pass strict testing to bring quality service to the Fort Myers Beach, FL area! Read review after review from your satisfied neighbors in Fort Myers Beach, FL.
for Fort Myers Beach, FL
Our Reviews by City
Tom - Fort Myers Beach, FL
Brandon Barahona was polite, friendly and knowledgeable about the job.
Phyllis - Fort Myers Beach, FL
John was fast. He explained everything he did, then checked to see if anything else was needed. Cleaned up any mess he made. I would recommend the service.
Mike - Fort Myers Beach, FL
Would use again
Great service, extremely expensive
Dave - Fort Myers Beach, FL
As mentioned above, the technician Brian was an excellent electrican and very friendly. However the service fees were way too expensive, not his fault. Brian was at our place for 2 hours and replaced 1 outlet, the rest was service fees, I guess about $450 worth. Or approximately $200 per hour and a $59 Service call.
Great service as always
Robert - Fort Myers Beach, FL
Same day service that can't be beat
Karen - Fort Myers Beach, FL
The guys were respectful, knowledgeable,,friendly, clean, helpful. I have never used Mr. Sparky before but was impressed.
Larry with Mister Sparky working on outlet Diagnoses in Fort Myers Beach
Larry with Mister a sparky working on generator transfer switch in fort Myers beach
Larry with Mister Sparky working on new circuit in Fort Myers Beach
New circuit for tiki hut fort Myers beach
Repairing 240v outlet in fort Myers beach Florida.
Install new breakers. Christian and rick
Larry with Mister Sparky diagnosing breaker in North Fort Myers
Installing ceiling fans in fort Myers beach, Florida.
Moving switches and outlets in fort Myers beach, Florida.
Install new security light provided by customer, Fort Myers Beach
Adding outlets. Fort Myers beach
Remove existing a swag chain ceiling fans installed new models on concrete ceiling with wire mold, Fort Myers Beach
Today the customer was concerned that she was interminet power loss on certain circuits. Larry was her on Sunday and replaced the main breaker. After looking at the distribution panel, I suggested a panel rejuvenation. This was suggested because the existing breakers were outdated and the breaker feeding this panel had corrosion on the lugs. There was also aluminum wires feeding this panel with no Aluminox on the connection. The panel rejuvenation was completed and all circuits are back working properly.
Today we replaced two defective outlets, and replaced smoke detectors, Inspected main electric panel, and gave options for solutions to permanent repairs
Came out on Sunday to see why the condo had no power.
Replacing a bad Pico remote in Fort Myers Beach
Surge Protection, fan installation and LED tape lighting
Installation of an outdoor ceiling fan.
Troubleshooting a newly installed boat lift motor.
Installed new three-way switch
Installed a 30 amp plug for a dryer with a breaker less than 30 feet
Troubleshooting partial power loss in a mobile home
Bathroom exhaust fan in Fort Myers
Drove down to see what's wrong with the generator.
Installing 3 3 phase 20 amp circuits for dryers