Extremely professional and personable, work was efficient and accurate… yes, I would certainly use Mr. Sparky again and recommend them to friends.
Mister Sparky provides on-time electrical services to the Lighthouse Point, FL area with pride. Don’t spend hours waiting on someone else — call Mister Sparky for same-day service!
Read our happy reviews from your Lighthouse Point, FL neighbors to see how we can help your family’s electrical problems.
for Lighthouse Point, FL
Our Reviews by City
James - Lighthouse Point, FL
Tech worker was very knowledgeable and professional.Hard worker !
Professional, knowledgeable and courteous.
Paul - Lighthouse Point, FL
Great experience !
Tim - Lighthouse Point, FL
Extremely professional!! Did more work then I originally needed because I figured as long as I have someone this good let’s take advantage!
Marianne - Lighthouse Point, FL
Gene - Lighthouse Point, FL
Selwyne arrived promptly and explained how the Mr. Sparly service is conducted as a homeowner I was a bit confused with regards to the fees for this service and although Selwyne was professional and completed the work both diagnostic and repair I was taken back when he informed me to the total cost for this visit ,I understand the slightly inflated price for the Breaker 60 amp and the service charge but in all honesty for what amounted to a under one hour service call and part $419.75 seems like quite an inflated price ...
Brandon with Mr Sparky
John Elvis - Lighthouse Point, FL
Barbara - Lighthouse Point, FL
Very great workmen!!!!!
Installed a new water heater whip. Installed a new 3 prong dryer outlet and connected a dryer cord that costumer supplied. Thanks for choosing Mister Sparky
Replace high hats in shower
Replace two broken gfci so
Installing led retrofits
Adding led retro fits.
New refrigerator circuit to the garage. Lutron caseta with pico remote. Supply and install outdoor flood light.
Install a floodlight and surge protection
Install new disconnect and sub panel. New grounding and interconnected smoke detector system. Surge protection. Permitting. Replace all outlets and swithces. New ground fault interruptors.
Replace meter base and main breaker panel. Replaced the main lug breaker panel and installed a new main grounding system. Interconnected smoke detectors were also installed.
Landscape light troubleshooting. Circuit diagnosis