Punctual. Honest. Gave several options for us to chose from. The electricians were very personable too!
West Palm Beach, FL prefers electricians at Mister Sparky for high quality work and customer service. Take a look at our reviews and find out why our electrical services are unrivaled in West Palm Beach, FL.
for West Palm Beach, FL
Our Reviews by City
Prompt and professional
Scott - West Palm Beach, FL
Nice guy and very fair
Joanne - West Palm Beach, FL
Man was polite friendly & professional. Waisted no time got right to business. We are very pleased
Great professional friendly service
Craig - West Palm Beach, FL
Great friendly service fast punctual neat clean & accommodating
Watch them every minute
Larry - West Palm Beach, FL
Good electrician, watch him every minute
Very honest, explained everything so I could understand it.
Suzanne - West Palm Beach, FL
Rene - West Palm Beach, FL
Customer service and techinian are great
Running wire molding for ceiling fan and fixing outlets
Replaced a faulty breaker and a new outlet in the laundry room. Also replaced an oversized breaker in the outside panel.
Replacing outlets and adding switch and replacing conduit for panel
Troubleshooting dishwasher and disposal
Replaced electrical panel, and installed smoke detectors.
Emergency call, partial power to home
Troubleshooted the problem and found out that the outside GFCI had a short on it. Cleaned the short and everything back to normal. Installed a new GFCI. Thanks for choosing Mister Sparky
Cut in a box and installed a new outlet in the bathroom for the TV. Installed a surge protector for the main panel
Installed 10 circuits generator panel with remote outlet. Replace with new 110V smoke detector. Installed a new surge protector for the panel per costumer request.
Today a dishwasher/disposal outlet was troubleshot. The issue was with a splice for the switchloop. I made a repair and installed a new single pole switch for the disposal. There was a concern with the main breaker in the indoor panel. I showed Jason and discussed options to replaced the panel.
Replaced a breaker in the panel to fix a potential hazard.